What is different on the NYB’s silenced mode unit?
The condenser fan speed is reduced by 20%.
Can I get the NYB from the factory in silenced mode?
Yes this can be done. The selection will need to be de-rated.
Can I reduce the water volume needed when I have multiple NYB’s together?
Yes when you have 3 or more NYB’s together you can reduce up to 30% of the water volume, depending on the application it is being used for. When doing this always ask Aermec to confirm. Please contact firstname.lastname@example.org for further information.
What is needed to control up to 9 NYB’s at once?
Multichiller (1 for up to 9 NYB’s) Modbus card for every unit.
What Controller does Aermec use in an NYB?
Carel PC05 and PGD1 interface.
Do the NYB’s have a single point power connection on multiple modules?
Not from the factory, but we can have this done with a third party.
How many NYB modules can be piped together?
What is the size of hydronic connections on an NYB?